Cause: The actual position loaded into the control counter when the reference position is
passed does not coincide with the reference position stored. The allowance
adjusted is also exceeded in this case (default = 0.008 cm).
This is caused by the loss of counting pulses during the backgauge run, or if the
mechanical reference switch detects "multiple" positions, or positions beyond the
range determined during the reference run.
On 78 ES, this error may be caused when the computer voltage is dropping
Remedy: - Make a reference run and move the backgauge along the entire width of the
table, if the position of the mechanical reference point switch has been modified
- Use service menu "machine data" for troubleshooting
- Check / replace pulse transducer
- Check cable routes / connection.
- Check / replace SAP- board.
- Check / replace CPxx- board.
- Check mechanical reference switch (flush version, id. no. 228472 on POLAR 66)
and switching flag. - Check power supply units G1 / G2 and replace, if necessary.
Let me know, any question or additional information if you Need
Automatically Autonomous Automation
Although the autonomous car is not quite ready, a lights out print operation is something you can do right now if you have a comprehensive Print MIS (Management Information System). The advantages can put money on your bottom line. So what’s your next step?
Link to Article